Note: To be installed by a qualified tradesperson in accordance with manufacture's instructions and AS/NZS 3500 plumbing and AS/NZS 3350 wiring regulations.
Location: The tap should be positioned either on a suitable sink or on the optional tap font. Undersink unit should be located directly under the tap- maximum up to 1 metre away. The undersink unit must be installed with clearances of 50mm left and right, 220mm above and 65mm rear. Fnt installation may be suitable for placement over drawers and dishwashers and for disability access. Refer installation instructions for detail.
Plumbing: Designed for direct connection to a potable cold water supply with a minimum pressure of 70kPa and a maximum pressure of 700kPa. If static pressure exceeds 700kPa, a 500kPa pressure limiting valve must be fitted. An isolating valve should be installed between the water supply and the under bench unit.
Venting: A vent in the tap head may discharge small amounts of water or steam so the tap must be mounted where it can drain. The cupboard containing the operationl unit must be amply ventillated.Cupboard doors should be offset for ventillation using 4mm buffers provided. A ventillation grill is also provided with each unit for high usage applications. When installing the unit where minimum clearances are met, instalation of an auxiliary exhaust fan accessory is strongly recommended (comes standard with Product #73165 and must be fitted)
Electrical: To be connected to a 10amp GPO, 220V-240V AC power supply.
Caution: In some hard water areas where mineral scale accumulation can become a problem, consideration should be given to the maintenance required. A suitable form of water treatment may be necessary