Note: To be installed by a qualified tradesperson in accordance with manufacturer's instructions and AS/NZS 3500 plumbing and AS/NZS 3350 wiring regulations.
Location: The tap should be positioned at the rear of the sink. The tap should be mounted on a flat surface. A 25mm diameter cut-out is required for fitting. Under sink chiller should be installed with clearances of 60mm left, right, rear and above. Filter should be mounted where readily accessible on the chiller or on the adjacent cupboard wall.
Plumbing: Water connections 12.7 mm BSP. Designed for direct connection to a potable cold water supply with a minimum presure of 70kPa and a maximum pressure of 700kPa. A 500kPa pressure reducing valve must be installed if water supply pressure is likely to exceed 700kPa
Venting: The cupboard containing the operational unit must be amply ventilated. Cupboard doors should be offset for ventillation using 4mm buffers provided. A ventilltion grill is also provided with each ubit for high usage applications. When installing the unit where minimum clearances are met, installation of the auxiliary exhaust fan accessory is strongly recommended.
Electrical: To be connected to a 10amp GPO, 220V-240V AC power supply